Power Transformer Monitoring
Installing an NK Technologies’ Current Transducer over the conductors on the secondary of a transformer can be used to alarm if the current draw reaches a critical level. Action can then be taken to reduce the load before the transformer overheats.
Most large power transformers utilize auxiliary cooling fans, drawing cooler air from a distance away from the transformer. NK Technologies’ Current Transducers or Current Operated Switches are used to monitor these fans for overload from bearing failure, under loads from drive component breakage or slippage, and to just be sure that the fan is energized and doing its required job.
Equipment Ground Fault Monitoring
As we become more aware of occupational health and safety so the need for protection against ground faults is growing. Industrial electrical equipment is fed via a distribution system which in turn is connected to a main feed. Ground fault protection may be installed, for instance at a main breaker, protecting the branch circuit but not necessarily a valuable or critical piece of equipment. Industrial Ground Fault Sensors from NK Technologies are designed to be installed in individual pieces of equipment or their electrical feed. The sensors provide an on/off output that may be used to operate a circuit interruption device like a shunt trip breaker or feed into an alarm system. With over 100 models to choose from, there’s sure to be one to fit your application.
The need for back-up power for critical loads is becoming more and more apparent to operating and maintenance personnel. Many existing factories and facilities are also adding generators to assist the grid connection supply during times of excessive consumption, or to help the plant ride through periods of peak usage when the utility charges a premium for power. Monitoring the current demand provided from a generator allows for load shedding of non-critical loads when the generator is nearing its capacity. NK Technologies’ Current Operated Switches close when the demand, measured by current, is too high, and by connecting to a controller (like a PLC), less critical loads can be disconnected from the system.
Critical Lighting Systems Preventative Maintenance
High technology lamps have been developed for a variety of specialized industrial and commercial applications. These lamps are expensive and their useful life should be maximized. Installing an NK Technologies’ Current Transducer to measure the current draw of a lamp provides the information to determine the lamp’s condition by comparison to known characteristics. Intelligent control devices, like PLCs, are programmed to adjust the applied voltage or current to optimize the life of the lamp.
Vacuum Pump Monitor
Vacuum pumps are used in a variety of applications in the semiconductor industry, heat treatment, plastics and packaging industries. By adding an NK Technologies’ Current Transducer over the lead feeding a vacuum pump, it can easily be determined when all the air has been removed from a vessel or envelope. The analog output can signal the vacuum or equipment controller that it is time for the next step in the process. In the case of an automated packaging machine, a drop in current will signal that the package is ready for sealing.
The auxiliary contacts in a motor starter are commonly used to indicate when the motor is running. However, auxiliary contacts only indicate the position of the contactor, not the actual load status. If a downstream disconnect is open (for example, for maintenance) or the contact fails (either sticks or dirt build-up) there can be serious consequences.
At a large fish farm, failed aerator pumps resulted in massive stock losses. Because the auxiliary contacts remained closed when the pump failed, the alarm was never activated, the back-up pumps were not switched on and the fish suffocated due to lack of oxygen. Now NK Technologies’ Current Operated Switches have been installed to provide an alarm signal and a signal to automatically switch over to the back-up aerator pumps.