With ever increasing demands for electrical power the power generating companies are beginning to penalize customers with low Power Factors. Low PFs can be considered very inefficient use of electrical energy. A low PF can be corrected by the installation of PF Correction capacitors. Although this can be achieved at the main feeder most facilities, due to multiple varying loads, choose to install PF correction on individual pieces of equipment (like a large motor) or area of plant. When a load is switched off, unless the PF correction capacitors are removed, undesirable over-correction occurs. Sophisticated automatic control systems are available but are very expensive. A simple way to switch a PF correction capacitor bank is to use an NK Technologies’ Current Operated Switch. When the load goes down, for example at night when equipment is not used, the PF correction capacitor is switched out. Then when load returns it is switched back in.
Installing an NK Technologies’ Current Transducer over the conductors on the secondary of a transformer can be used to alarm if the current draw reaches a critical level. Action can then be taken to reduce the load before the transformer overheats.
Most large power transformers utilize auxiliary cooling fans, drawing cooler air from a distance away from the transformer. NK Technologies’ Current Transducers or Current Operated Switches are used to monitor these fans for overload from bearing failure, under loads from drive component breakage or slippage, and to just be sure that the fan is energized and doing its required job.
The need for back-up power for critical loads is becoming more and more apparent to operating and maintenance personnel. Many existing factories and facilities are also adding generators to assist the grid connection supply during times of excessive consumption, or to help the plant ride through periods of peak usage when the utility charges a premium for power. Monitoring the current demand provided from a generator allows for load shedding of non-critical loads when the generator is nearing its capacity. NK Technologies’ Current Operated Switches close when the demand, measured by current, is too high, and by connecting to a controller (like a PLC), less critical loads can be disconnected from the system.